septic tank and absorption pit with details of manholes and inspection.
Drawing labels, details, and other text information extracted from the CAD file (Translated from Spanish):
Until finding permeable soil, Study drawing:, Ing. F.w.d.p, draft:, content:, scale:, Indicated, date:, May of, sheet:, Vo.bo., located in:, content:, Detail of septic tank absorption well, Septic tank plant, Esc:, section, Esc:, unscaled, Variable until finding permeable soil, Permeable soil, Until found, Support rods, of the tube, Soil level, Concrete pipe, Of diameter, Perforations, Absorption well detail, ball, stone, Comes from septic tank, Reinforcement no., Slab thickness, Links, Smoothed with cement ratio, Chamfer with mortar, entry, departure, Registration box with concrete lid, air chamber, water level, Absorption well, Concrete slab reinforced in both directions, Final sill ref. Esl., Ventilation system, Pvc, Cleaning mouth with concrete lid, Perimeter est., detail, Esc:, detail, Esc:, General notes the sewage system will deposit the sewage to the septic tank system. The pipelines of the pending alignments indicated in the drawings should never be installed less than in all the external installations should be used polyvinyl chloride pvc pipe. The boxes must not be built until the piping flush structures are defined. Under no circumstances should drainage of the sanitary drainage system discharge any rainwater. Before placing the newly constructed septic tank service should be filled with water if possible pour about five buckets with sludge from another septic tank to accelerate the development of anaerobic organisms. The septic tank should be inspected every six months. When opening the septic tank register to carry out the inspection inspection, fifteen minutes should be allowed for adequate ventilation. Never use torch matches for inspection. The septic tank is not disinfected and only the sludge must be removed., row, In each cell with fluid concrete casting, reinforcement, Pvc, Vent tube, Block row
Raw text data extracted from CAD file:
|Category||Water Sewage & Electricity Infrastructure|
|Building Features||Car Parking Lot|
|Tags||absorption, autocad, DETAIL, details, DWG, inspection, kläranlage, manholes, pit, septic, septic tank, tank, treatment plant, well|